11/8'' ODF Port Size MSV-1099/9 Refrigeration Solenoid Valve In
Our MSV-1099/9 refrigeration valves are available in a wide range
of fluoride refrigerants, and we also offer ammonia refrigeration
valves.The MSV refrigeration solenoid valve used in liquid,suction
and hot gas lines with fluoridated refrigerants.That is an
automatic control parts used in refrigeration system to control the
refrigerant to pass or not pass.
Technical information of G1 1/8'' MSV-1099/9 refrigeraiton solenoid
|Connection||G 1 1/8 Inch |
|Max. opening pressure||2.5 mpa|
|Min. opening pressure||0.05 mpa|
|Working pressure||3 mpa|
|KV value||5.7 m³/h|
|Length||106 mm |
Overall dimension of MSV-1099/9 G1 1/8 Inch Refirgeration solneoid
valve as an automatic control parts:
Internal display of MSV1099/9 Refrigeration electromagnetic valve
Diaphragm and pilot of MSV1099/9 solenoid valve in refrigeration
Nomal problems of ice maker machines with MSV-1099/9 refrigeration
solenoid valves in Air-conditioning:
Symptom 1: No ice or ice is not smooth.
Analysis and repair: If the ice machine can not enter the deicing
state, it indicates that the control part has failed. At this time,
adjust the ice thickness knob first to see if the ice thickness
changes. If it changes, it indicates that the ice thickness
detector is normal and the cause of the failure. The electrical
control board is damaged, otherwise the ice thickness detector is
If the ice machine can enter the de-icing state and cannot be
detached smoothly or the ice-free time is too long (more than 5
minutes), the reasons are as follows: 1. The foreign matter
attached to the surface of the evaporator is not conducive to ice
making and ice-removing. Clean the evaporator surface, the water
sprinkler and the water storage box; 2. Refrigerant leakage; 3. The
heating valve has failed and cannot be opened.
Symptom 2: Some ice cubes are incomplete in shape.
Analysis and overhaul: The cause of the failure is that the nozzle
hole is blocked, resulting in poor water flow in the spray pipe. In
the state of ice making, use the tweezers to remove the debris in
the water outlet hole of the spout, and make the flow in each hole
as smooth as possible.
Symptom 3: No ice is produced.
Analysis and repair: The reasons for the failure are: 1. The
machine is not placed horizontally, then it can be placed
horizontally as required; 2. The ice thickness detector is damaged
or the thickness of the adjustment is too small; 3. Solenoid valve
is damaged; 4. The refrigerant leaks.
Symptom 4: The pump works, but it does not water.
Analysis and repair: The reasons for the failure are: 1. There is
air in the pipeline, and the air in the pump can be discharged; 2.
There is too much ice slag at the bottom of the tank. At this time,
it is necessary to stop the discharge of ice slag and then restart
it. The internal impeller of the pump is seriously worn and the
pump needs to be replaced.
Symptom 5: It is not easy to get rid of ice.
Analysis and repair: The reasons for the failure are: 1. The flow
rate of the upper water is small or the water supply valve is
broken; 2. The heating valve is bad or the heating is insufficient;
3. The surface of the evaporator is too dirty, that is, the scale
is too much; The thickness of the ice block setting is too thick.
Symptom 6: Water replenishment cannot be performed automatically.
Analysis and overhaul: First check the water inlet condition of the
pipeline. If it is not water, turn on the water source and restart
it. If the inlet pipe is normal, it indicates that the inlet
solenoid valve is faulty and needs to be replaced.
Welcome to your inquiry!